Description for Honeywell R7861A1026
Overview:Flame failure response time of 0.8 or 3.0 seconds.
Flame signal strength ranges from 0.0 to 5.0 Vdc.
Plug into 7800 relay module through printed circuit board edge connector keyed for proper orientation.
Flame signal test jacks to measure amplifier flame signal voltage.
Color-coded labels identify flame detection type. Dynamic Self-Check Amplifier test the detectors and all electronic components in the flame detection system 7800 SERIES relay module locks out on safety shutdown with flame detection system failure.
Compatible with existing Honeywell flame detectors (order separately).
Solid state plug-in amplifiers that respond to flame detector inputs to indicate the presence of flame when used with 7800 SERIES relay modules.
Flame Failure Response Time (sec): 2.0 sec or 3.0 sec
Self Checking: Dynamic Self-Check
Use With Primary Safety Control: 7800 SERIES Relay Modules
Use With Flame Sensor: Gas, oil, coal: Ultraviolet Flame Sensor C7061