- Defrost initiation is adjustable from 1-8 cycles per day; minimum three hours between successive cycles.
- Delay or pump down cycle is adjustable from 0-30 minutes; 3 minute graduation: for stopping fans, reducing refrigerant pressure, or hot gas pump down cycle.
- 3-45 minutes defrost cycle; 3 min. graduation.
- Drain or fan delay cycle is adjustable from 3-15 minutes; 3 minute graduation.
- Sequence switching: 2 NO 2 NC.
- Switch ratings: 10 amps, 345 VA pilot duty 120-240 Vac. Switches 2-4 and 3-4 carry 1/2 Hp rating.
- Heavy steel gasketed case; gray finish, knockouts on bottom, side and back; hasp and staple for padlock. Available on bracket for sub-panel mounting
- Ru recognized and CSA approved.