|Flow Rate (GPM):||
|Number of Plates:||
|Max Pressure (PSI):||
up to 1200 BTU/H/oF-sq ft
|Cover Plate Material:||
|Temperature Range (F):||
GEA Flat Plate's FP series of Heat Exchangers is designed for hydronic heating, snowmelt (glycol), potable hot water, various industrial processes and other uses where an efficient, reliable and compact fluid-fluid heat exchanger is required. These heat exchangers are 100% factory tested, are made of stainless steel, and have heavy duty male pipe thread connections, and mounting studs come standard. The heat exchangers are UL and CRN listed.
The FP Series is designed for a wide variety of fluid to fluid applications requiring exacting heat transfer performance. Hydronic Applications include:
Capable of 8F to 10F approach (std) to as low as 3F approach for the larger models. Totally sealed stainless steel construction, copper brazed with a high performance heat transfer surface to promote low fouling. From 1/2 to 200 gpm models, and larger sizes to 400 gpm. ALL models have MPT male pipe thread connections and mounting stud bolts. Rated at 450 psi working pressure, both sides. U.L. Listed, European TUV and optional ASME code construction. The FPN Series Heat Exchanger is similar, except that it is Nickel Brazed. The FPN is ideal for de-ionized water, solvents and other applications. Rated at 300 psi working pressure.
Reviewed by 1 customer
Displaying review 1
Comments about 14 plate, 3/4" Thread, 8 GPM Heat Exchanger (3" x 8"):
This was to replace an existing heat transfer for a solar hot water system. Old one after about 10yrs, was all gunked up and not functioning. This one brought the system back to producing 140 degree water!
Do you have questions about this product?
Get answers from real customers and in-house experts with AnswerBox.
Q:Of the individual ports witch pairs are for fluid a and fluid b.
A:Ports one and two are Fluid A, 3 and 4 are Fluid B.
Q:what is the btu output of the 3x8 14 plate?
A:here is a link to the manual w that data. there are many variable to calculate the BTU
Q:May this heat exchanger be used with glycol and water, i.e. glycol circulating through solar paneL unit and water to/from hot water heater or water storage tan?
A:Yes, it can be used for such an application.
Q:Where is this heat exchange made and what is the warranty?
A:This heat exchanger is made in the United States and has a one-year warranty.