For frozen goods, it automates the defrosting process according to the needs of the facility (intelligent defrosting), providing energy savings. It operates with two sensors, one for room temperature and the other, fastened to the evaporator, that controls defrosting completion and fan restarting. The room temperature control has a normal setpoint and an economy setpoint, in addition to the fast freezing functionality and alarm functions indicating that the door is open. It features up to two digital inputs. One of these inputs may be configured as sensor 3* to monitor the condenser temperature and disconnect the control outputs in case of an alarm. It also features a digital filter, which is intended to simulate an increase of the mass of the room temperature sensor (S1), thus increasing its response time (thermal inertia), and avoiding unnecessary compressor activations. Its 16-Amp relay output can control compressors of up to 1 hp and the defrost output has a current capacity of 10 Amp. To drive inductive loads (motors and pumps) of up to 2 HP, use model TC-900E 2HP.
- Cold Storage Rooms
- Display freezers